This paper addresses the difficulties in pinpointing reasons for unexpectedly high energy consumption in construction, and in lowenergy houses especially. Statistical methods are applied to improve the insight into the energy performance and heat dynamics of a building based on consumption records and weather data. Dynamical methods separate influences from outdoor temperature, solar radiation, and wind on the energy consumption in the building. The studied building is a lowenergy house in Sisimiut, Greenland. Weather conditions like large temperature differences between indoors and outdoors throughout long winters, strong winds, and very different circumstances regarding solar radiation compared to areas where lowenergy houses are usually built, make the location very interesting for modeling and testing purposes. In 2011 new measurement equipment was installed in the house, which will be used to develop more detailed models of the heat dynamics and energy performance in relation to different meteorological variables, heating systems, and user behavior. This type of models is known as a graybox model and is been introduced in this paper.
Lowenergy houses ; Heat dynamics ; Arctic climate ; Statistical modeling ; Graybox modeling
Increasing consciousness of the impact of human activities on the global environment – namely the consequences of emissions of greenhouse gases – has lately led to political goals of lowering energy consumption and switching to more sustainable energy supply systems. In buildings, this calls for improved methods for assessment of energy performance and characterization of heat dynamics.
In order to lower costs of collecting digital consumption data and for the consumer to be able to monitor his or her consumption pattern and maybe even adapt to price fluctuations, online data collection devices such as “Smart Meters” are getting increasingly common in dwellings. They typically monitor and log at least one consumption variable and possibly indoor climate variables. Already in Westergren et al. (1999) a framework is developed to estimate physical parameters of buildings based on weather and consumption data, and the energy consumption is modeled for a sample of buildings. In Mortensen and Nielsen (2010) rather simple methods are presented on how to estimate UAvalues, gAvalues and sensitivity to wind speed of buildings using only consumption and weather data. In Bacher et al. simple lowpass filters are applied to inputs and outputs in order to obtain reliable predictions of heat consumption in buildings on time intervals down to 1 h.
Discretetime dynamical models have a large potential for use on automated and standardized measurements. ARMAX (Autoregressive Moving Average with eXogeneous inputs) models are a wide class of dynamical linear models. Norlén (1990) implements a recursive algorithm to estimate the UAvalue of a test cell with ARMAX models, and in Jiménez et al. (2008a) ARMAX models are used on data from a test wall.
More detailed information about the heat dynamics of a building can be achieved by applying continuoustime models such as graybox models to data of higher resolution. This has been done for a part of a highly insulated building in Madsen and Holst (1995) . In Andersen et al. (2000) it was applied on a multiroom building, and Bacher and Madsen (2011) present a method for a consistent model selection procedure.
In 2005, a lowenergy house was inaugurated in Sisimiut, Greenland. The objective was to build a house with very low energy consumption for heating, which should inspire the development of energyefficient housing in Greenland and demonstrate the potentials for energy efficiency in a house which should also be a leading example of good indoor thermal environment. The house and its objective was also to be presented in Norling et al. (2006) . Therefore the current paper will only briefly introduce the building and then focus on how well the house has lived up to its performance targets, and which challenges it has incurred. Some preliminary performance results were presented also in Rode et al. (2009) , but significant improvements have occurred since then. The statistical analysis will be performed on data from before and after the work was conducted on the building and the results will be compared.
Apart from improvements on the energy performance of the envelope, the building has been equipped with numerous sensors and control equipment for conducting experiments in the building. Long winters of low outdoor temperatures give a high signal/noise ratio and ease planning of experiments. The modern design of the building with a high level of insulation, large window areas, and floor heating makes it interesting for studies of heat dynamics of modern lowenergy construction. Moreover, it consists of two symmetrical apartments which enable studies of the influence of occupancy.
This paper presents results of statistical modeling of historical consumption data from the house in order to quantify the alleged improvement of the building envelope. It also describes the new measurement setup, and finally presents suggestions for obtaining more detailed heat dynamic models. The paper is structured in the following way: Section 2 gives a brief presentation of the lowenergy house, Section 3 describes a statistical methods for analysis of data before and after the repair work on the building. Section 4 lines out plans for future experiments and analysis, and finally conclusions are given in Section 5 .
A target for the house was that the energy consumption for heating and ventilation should be only half of that permitted by the 2006 version of the Greenlandic Building Regulations: 230 kW h/m^{2} /yr (Government of Greenland, 2006 ). Furthermore, considering that the house was planned to have a ventilation system with heat recovery – something that was not assumed for residential dwellings in the building regulations – the target value 80 kW h/m^{2} /yr was chosen. Building energy simulations were executed to substantiate that this level of annual energy consumption was possible. The means to reduce the energy consumption in comparison with common Greenlandic houses have been to use extra insulation in floors, exterior walls and the roof. Advanced windows have been used with low energy glazing using normally 3 layers of glass. A solar collector has been installed on the roof for domestic hot water heating. The house has been orientated to exploit the light and its geometry optimizes the daylight absorption. The ventilation system is supplied with a counterflow heat exchanger that uses the warm exhaust air to preheat the cold inlet air. Sisimiut is the second largest city of Greenland (5500 inhabitants) located on the west coast just 42 km north of the Polar Circle. The mean average temperature is around 6 °C in summer and around −13 °C in the winter months. The number of heating degree days is around 8000 Kdays (base 19 °C). The house is approximately 200 m^{2} and is made as a semidetached house, where the two living areas are built on each side of the boiler room and an entrance hall. Figure 1 shows a picture of the house, and Figure 2 shows the cross section and floor plan. One of the two dwellings serves as home for a family, while the other is used as a guest house for visitors and for research experiments.

Figure 1. Photo of the lowenergy house in Sisimiut as seen from the west.


Figure 2. Cross section and floor plan of the lowenergy house. The house is built as a double house with common scullery/boiler room and entrance hall.

The building is generally made as a wood frame construction. The inhabited part is all on one floor, which is distributed over two slightly displaced levels, and there is a cold attic above the whole building, and an open crawl space below. The heat loss due to thermal transmittance of the building envelope constructions is kept at a minimum by using large insulation thicknesses and wooden posts and girders in two separate layers that do not touch each other, so thermal bridges are practically eliminated, see Table 1 and Figure 3 . As it can be seen from Table 1 all the constructions have Uvalues below the demands.
Construction  Floor  Walls  Roof 

Insulation thickness (mm)  350  300  350 
Uvalue calculated (W/m^{2} /K)  0.14  0.15  0.13 
Uvalue GBR 2006 (W/m^{2} /K)  0.15  0.20  0.15 

Figure 3. Wood based structural members near a corner of the building are configured such that thermal bridges are avoided. To the right: a plot of the calculated temperature distribution around the corner. The calculated linear thermal transmission coefficient is Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \psi =0.015\quad W/(m\quad K)} .

Three types of glazing units are used in the lowenergy house:
Type 1 1+2 solution: Made of one single glass layer with a hard lowemission coating and a sealed unit with two glass layers.
Type 2 Combined double energy glazing and a vacuum glazing unit.
Type 3 2+1 solution: Made of a sealed unit with two layers of glass and a separate single layer of glass with a hard low emission coating.
The three types of glazing units are shown in Figure 4 . Data for the glazing units are shown in Table 2 . The net energy gain is calculated as a mean value of windows oriented north, east, west and south for a reference house.

Figure 4. The three glazing units used in the lowenergy house.

Type  Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle U_g}
(W/(m^{2} K)) 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle g_g}
(–) 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle Q_g}
(kW h/m^{2} ) 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle U_w}
(W/(m^{2} K)) 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle g_w}
(–) 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle Q_w}
(kW h/m^{2} ) 

1: 1+2  0.7  0.45  172  1.0  0.30  −17.3 
2: 2+Vac.glaz  0.7  0.40  136  1.1  0.27  −59.3 
3: 2+1  0.8  0.56  228  1.1  0.47  67.1 
The lowenergy house is constructed with a hydronic floor heating system based on PEXtubes installed in aluminum plates just below the wooden floor boards. The floor heating system in the bathrooms is based on PEXtubes cast in the concrete. The ventilation system is equipped with a heating coil which is positioned in the supply air duct after the heat exchanger. The heating coil is meant to ensure that the air supply is at a minimal temperature of 18 °C. The ventilation systems heating coil is based on the same hydronic system as the floor heating.
Hot water for the floor heating and heating coil is supplied from an oil furnace, which is located in the boiler room of the house. Heat for the domestic hot water comes from a solar collector. The oil furnace supplies back up heat in periods when the solar heating is insufficient. Finally, a radiator in the entrance hall is meant to be heated with excess heat from the solar collector system when available.
Mechanical ventilation with heat recovery in cold climates can present problems with ice formation in the heat exchanger. When warm humid room air is brought in contact with the cold surfaces of the exchanger (cooled by the outside air), the moisture in the exhaust air condenses in the heat exchanger. If the outside air is below freezing, the water vapor will freeze, resulting in a larger air flow resistance on the exhaust side of the exchanger, which in turn decreases the air flow. The decrease in the amount of warm air through the exchanger will result in the exchanger being cooled further, and eventually the system will become fully blocked with ice and stop. This problem can be prevented by preheating the inlet air before it reaches the exchanger. This will however result in extra energy consumption and higher installation costs, and is therefore not an optimal solution.
A new design of a heat recovery unit was developed for the lowenergy house in Sisimiut in cooperation between EXHAUSTO A/S and the Technical University of Denmark. The dimensions of the unit are length 1760 mm, width 930 mm and height 660 mm. The unit consists of two highly efficient aluminum counter flow heat exchangers coupled in a serial connection. A damper is able to switch the air flow direction through the units. When ice formation starts to reduce the air flow in the coldest exchanger, the air flow direction is switched. The exchangers, damper and filters are mounted in a cabinet with 50 mm insulation, although the unit is recommended to be placed in a heated place to minimize risks of frost damage from the condensing water. A diagram of the system is shown in Figure 5 . The theoretical temperature efficiency of the heat recovery unit is approximately 90%.

Figure 5. Diagram of the heat recovery unit with two heat exchangers. A valve and a timer switch the flow direction when ice formation reduces the air flow.

Solar hot water panels installed on the lowenergy house constitute a flat plate collector. It has a total surface area of 8.1 m^{2} and the system is able to collect 1700 kW h/yr. This covers approximately 57% of the hot water consumption of the house. The house and its inhabitants use around 150 L of hot water per day. The solar collector faces southeast and is tilted 70° from horizontal to have the optimal position in relation to the sun.
Since the completion of the house, consumption and some indoor climate variables have been measured. The consumption recordings consist of common oil consumption and electricity consumption recordings for each apartment and for common areas. For the ventilation and heating systems, all inlet and outlet flows and temperatures have been measured. Moreover, measurements have been taken for temperatures and relative humidity both indoors and in some construction parts. Consumption recordings are cumulative, temperature and flow measurements are instant, and all data were logged every hour. Unfortunately, the measurement recordings have been interrupted, which limit the periods which can be used for modeling.
Two periods of approximately 2.5 months each have been chosen for analysis. The first period starts on September 1, 2009 while the second starts on February 1, 2010. Mending had been carried out between these two periods so the house was expected to perform better – namely be tighter and have a better control of the heating – in the second period.
A first comparison of the energy consumption for the two periods is seen in Figure 6 . The largest power consumption is in floor heating which has been reduced by 545 W on an average or more than 15%. The ventilation heating is in general only 510% of the contribution from floor heating but it has increased by around 35%. Energy consumption for water has dropped significantly by 69%. All three electricity consumptions have increased. While for a household all power consumption is equally interesting, in the modeling of the performance of the building envelope, hot water consumption will be left out. This is because the hot water consumed is largely assumed to be drained while still warm. Omitting heating of domestic water, the average (heating and electricity) power consumption is 158 W lower in period 2 compared to period 1, which corresponds to a reduction of 3.5%.

Figure 6. Distribution of the power consumption in the building in the two considered periods.

The energy performance is hard to compare between periods because of the different weather conditions, possible differences in the use of the house, etc. For this reason, a statistical model is needed to describe the influences of different variables. The variables that will be used here are indoor and outdoor temperatures, solar radiation, and wind speed. The use of the building is assumed to have been similar in the two periods. The increased energy consumption for heating of water could suggest more occupancy in the second period, though.
An average UAvalue for the building is of special interest. The average UAvalue is interpreted as the steadystate heat conductivity of the envelope. Using only indoor and outdoor temperatures and solar radiation, this interpretation yields the following steadystate expression for the heat loss, Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle P_h}
, through the envelope:

( 1) 
However, the system is never in steady state and hence must be modeled with dynamic techniques. The UAestimate is then derived as the steady state response of the temperature difference to the heat consumption. A dynamical relation between the heat consumption and indoor temperature, outdoor temperature, and solar radiation can be modeled with an ARMAX model of the heat transfer at time n :

( 2) 
where A , B_{1} , B_{2} , B_{4} , and C are polynomials, and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle q^{1}}
is the backward shift operator given by

( 3) 
and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \lbrace e(n)\rbrace }
is Gaussian white noise. Notice that Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \lbrace n\rbrace } is discretetimenormalized so that the sample period equals 1. The parameters in the Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle B_1,B_2,B_3} polynomials are any real numbers, while Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle a_1=c_1=1} . For the system to be stable, the roots of Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle A(q^{1})} must lie within the unit circle. See Table 6 for nomenclature. Indepth treatment of ARMAX processes can be found in Madsen (2008) .
Symbol  Explanation 

A ,B_{i} ,C  Polynomials 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle C_h}  Thermal capacity 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle P_h}  Heat and electricity input 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle P_s}  Solar radiation 
R  Thermal resistance 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_a}  Outdoor temperature 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_d}  Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_iT_a} 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_i}  Indoor temperature 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle UA}  Common Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle UAvalue}
for the building envelope 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \overset{\mbox{ˆ}}{UA}}  Estimate of Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle UA}
value at W_{s} =0 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\overset{\mbox{ˆ}}{UA}}_{max}}  Estimate of Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle UA}
value at Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle W_s=8\quad m/s} 
Y  Observation 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle W_s}  Wind speed 
c_{w}  A constant related to the effect of wind speed 
n  Day number 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle q^{1}}  Backward shift operator 
Since the temperature difference is included in (2) through both indoor and outdoor temperatures, the UAvalue can be estimated both as the estimated stationary response from Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_i}
to Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle P_h} and as the negative stationary response from Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_a} to Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle P_h} . Compare with (1) for the sign convention.
The discretetime transfer function, H (z ), is given in the z domain as

( 4) 
where Y and X are Ztransforms of the discretetime processes Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \lbrace x_n\rbrace }
and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \lbrace y_n\rbrace } . For general treatment of signal processing and the z domain, see e.g., Oppenheim et al. (1983) and Madsen (2008) . In the (discrete) time domain, the impulse response Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \lbrace h_k\rbrace } is given as

( 5) 
The steady state response is the step response for time going to infinity. Since for the step response, x_{k} =0 for Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle k<0}
, and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle x_k=x} for Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle k\geq 0} , the steady state value of y becomes

( 6) 
where causality of the system is assumed (h_{k} =0 for Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle k<0}
).
Since the transfer function in a causal system can be calculated from the impulse response function as

( 7) 
it follows that

( 8) 
and so the step response simplifies to

( 9) 
Since the UAvalue is the steady state extra heat transfer when the temperature difference increases by 1 °C, this further simplifies to

( 10) 
in this case.
Hence – given that the considered process is stationary – the steady state value of the step response from Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_a}
to Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle P_h} is given by the transfer function from Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_a} to Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle P_h} for z =1:

( 11) 
The steady state value of the step response from Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_i}
to Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle P_h} is given by

( 12) 
To obtain an estimate of the UAvalue as the steady state response of the heat consumption to a step in difference between indoor and outdoor temperatures, the two estimates from Eqs. (11) ; (12) must be combined. The linear combination of the two yielding the lower variance is used. This is the estimate

( 13) 
where

( 14) 
The variance of the linear combination of the two estimates of Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle UA}
is calculated and minimized. The variance is

( 15) 
And the minimization yields

( 16) 
Notice that Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \lambda }
is unconstrained on Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle R} . The estimate cannot directly be interpreted as a weighted average of Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\overset{\mbox{ˆ}}{UA}}_{T_i}} and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\overset{\mbox{ˆ}}{UA}}_{T_a}} , since Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \lambda } can exceed Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle [0,1]} . This will happen when Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle Cov({\overset{\mbox{ˆ}}{UA}}_{T_i},{\overset{\mbox{ˆ}}{UA}}_{T_a})>V({\overset{\mbox{ˆ}}{UA}}_{T_a})} .
The variances of Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\overset{\mbox{ˆ}}{UA}}_{T_i}}
and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\overset{\mbox{ˆ}}{UA}}_{T_a}} and their covariance can be estimated by linearization (Westergren et al., 1999 ). Let Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \overset{\mbox{ˆ}}{x}} be the estimated parameters of an ARMAX model, and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle V(\overset{\mbox{ˆ}}{x})=P} . Then the vector of the estimates, Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\overset{\mbox{ˆ}}{UA}}_{T_i}} , Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\overset{\mbox{ˆ}}{UA}}_{T_a}} , is given by a possibly nonlinear but differentiable function, f , of Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle x} :

( 17) 
The variance–covariance matrix of the vector of estimates can be approximated by the firstorder Taylor expansion:

( 18) 
where Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \partial f/\partial x}
is the Jacobian matrix. While Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \overset{\mbox{ˆ}}{P}} can be estimated from the estimation of Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle x} , the Jacobian can be derived from f , in this case by differentiating the expressions (11) ; (12) . It is possible to estimate the variances of (11) ; (12) without linearization, see e.g., Tellinghuisen (2001) . The advantage of using (18) is that it yields the covariance between the estimates directly.
Time constants summarize valuable information about the dynamics of a system. Consider the linear first order system

( 19) 
The discrete time solution to this system is

( 20) 
where Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \Delta t}
is the sampling period, and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \tau } is the time constant.
For each pole, Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\phi }_i}
, of the transfer function of an ARMAX model, the corresponding time constant can be identified by solving

( 21) 
for Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\tau }_i}
.
In Mortensen and Nielsen (2010) the following model is used to estimate both UA and gAvalues based on daily average data. Let Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_d(n)=T_i(n)T_a(n)}
:

( 22) 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle UA=({UA}_1+{UA}_2)/2}
. n is the day number, and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \lbrace e\rbrace } is the white noise. This is clearly a submodel of (2) . The work in Mortensen and Nielsen (2010) is based on measurements where only the outdoor temperature was measured (and the indoor temperature was estimated). In the data from Sisimiut, indoor temperature measurements are available, however, and instead of using only the outdoor temperature, the difference between the indoor and outdoor temperatures can be used.
Now let Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle WT(n)=W_s(n)\cdot (T_i(n)T_a(n))}
and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle q^{1}WT(n)=W_s(n1)\cdot (T_i(n1)T_a(n1))} . Including an autoregressive term, this leads to the model

( 23) 
where Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \lbrace e(n)\rbrace }
are independent and for all n : Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle e(n)\sim N(0,{\sigma }^2)} . This model will be fitted to the two periods of data. The estimates of the Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle UAvalues} are calculated as in Eqs. (13) ; (14) .
The indoor temperature is the average of a temperature measurement placed centrally in each of the two apartments of the building. The heat input is based on an energy meter in the building measuring the energy dissipated in both floor heating and ventilation heating. The weather data are measurements from the local weather station in Sisimiut run by Asiaq (part of the Greenlandic Ministry of Housing).
The raw data has been averaged to daily values. Residuals of model (23) are plotted together with the averaged data for the two periods in Figure 7 . In the first period, the heat consumption is generally increasing as the outdoor temperature and solar radiation drop, whereas the opposite is the case in the spring (period 2). This is as expected. Three points from each data set were not well fitted and had too much influence on the parameter estimates (i.e., large Cooks distances, Ersbøll and Conradsen, 2005 ). Hence they were considered outliers and removed before the reported estimates were calculated. These points are indicated with red circles in Figure 7 .

Figure 7. Time series plots of average daily heating and explanatory variables for the first period to the left and for the second period to the right. The red points indicate outliers that have not been used for the model fits.

Model (23) was fitted to the data from the two periods omitting the classified outliers, and the parameter estimates are listed in Table 3 . Supporting the model parameters themselves, estimates of Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle UA}
 and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle gAvalues} are listed in Table 4 . The estimates of the UAvalues are calculated as in Eqs. (11) , (12) , (13) , (14) , (15) ; (16) , Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \overset{\mbox{ˆ}}{gA}={\overset{\mbox{ˆ}}{b}}_{3,0}} , and a parameter is related to the sensitivity to wind speed Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\overset{\mbox{ˆ}}{c}}_W={\overset{\mbox{ˆ}}{b}}_{4,0}} . Also, a property called Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\overset{\mbox{ˆ}}{UA}}_{max}} is reported. The term WT (n ) in Eq. (23) includes both W_{s} , Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_i} and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_a} . As it contains a product of inputs, it is a nonlinear term in the model. This makes the estimate of the UAvalue depend on wind speed. Hence, what is reported as Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \overset{\mbox{ˆ}}{UA}} is for W_{s} =0, and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\overset{\mbox{ˆ}}{UA}}_{max}} is calculated for Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle W_s=8\quad m/s} . Comparing Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \overset{\mbox{ˆ}}{UA}} and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\overset{\mbox{ˆ}}{UA}}_{max}} gives information about the sensitivity to wind speed, i.e., the tightness of the building. 8 m/s is chosen because it is a relatively high wind speed for both considered periods. For period 1 it corresponds to about the 0.97 quantile, for period 2, the 0.98 quantile.
Parameter  Estimate  Std. error  t value  Pr(Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle >\vert t\vert }
) 

Period 1  
a_{1} (–)  −0.40  0.11  3.80  0.000 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle b_{1,0}}
(W/K) 
−343.43  170.62  −2.01  0.048 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle b_{1,1}}
(W/K) 
420.36  160.51  2.62  0.011 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle b_{2,0}}
(W/K) 
−57.09  47.00  −1.21  0.229 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle b_{2,1}}
(W/K) 
−53.76  50.13  −1.07  0.287 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle b_{3,0}}
(m^{2} ) 
0.06  3.23  0.02  0.985 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle b_{4,0}}
(J/m K) 
9.07  2.33  3.89  0.000 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \sigma }
(W) 
735.41  
Period 2  
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle a_1}
(–) 
−0.29  0.08  3.58  0.001 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle b_{1,0}}
(W/K) 
203.87  116.69  1.75  0.085 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle b_{1,1}}
(W/K) 
−105.48  108.30  −0.97  0.333 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle b_{2,0}}
(W/K) 
−30.21  33.42  −0.90  0.369 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle b_{2,1}}
(W/K) 
−83.81  35.17  −2.38  0.020 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle b_{3,0}}
(m^{2} ) 
−6.28  1.67  −3.76  0.000 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle b_{4,0}}
(J/m K) 
10.43  2.42  4.31  0.000 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \sigma }
(W) 
658.62 
Property  Period 1  Period 2  

Est  Std. E.  Est  Std. E  
IndividualFailed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle gA}  
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \overset{\mbox{ˆ}}{UA}}
(W/K) 
88.9  23.5  103.3  14.9 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\overset{\mbox{ˆ}}{UA}}_{max}}
(W/K) 
161.5  23.5  186.8  14.9 
gA (m^{2} )  −0.1  3.2  6.3  1.7 
c_{W} (J m^{−1} K)  9.1  2.3  10.4  2.4 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \tau }
(days) 
1.0  0.8  
CommonFailed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle gA}  
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \overset{\mbox{ˆ}}{UA}}
(W/K) 
94.6  23.6  87.8  12.3 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\overset{\mbox{ˆ}}{UA}}_{max}}
(W/K) 
160.5  23.6  174.8  12.3 
gA (m^{2} )  5.7  5.7  
c_{W} (J m^{−1} /K)  8.2  2.2  10.9  2.4 
Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle \tau }
(days) 
1.0  0.8 
First, the full model in Eq. (23) is fitted to the two periods, one period at a time. The estimated physical properties for the two periods are shown in the upper half of Table 4 . Both Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle UA}
and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {UA}_{max}} increase from period 1 to period 2. However, notice that the gAvalue is Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle 6\times {10}^{2}\quad m^2} (not significantly different from zero) in the first period, while it is estimated to be around 6.3 m^{2} in the second period. This could be part of the reason for the large difference in the Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle UA} estimates. In the lower part of Table 4 a common gAvalue has been estimated. This is reasonable because the mending of the building did not include any changes related to the glass facades. On the other hand the surroundings may have changed, especially the reflectivity of the surroundings may have changed due to the change in snow cover and vegetation. Using the common gA estimate, there is a drop from 95 to 88 for no wind, but the estimate of UA increases from 160 to 175 for wind speed 8 m s^{−1} . However, these changes must be compared with the uncertainties of the estimates. For the models using a common gAvalue, neither UA, Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {UA}_{max}} , nor c_{W} are significantly different between the two periods using t tests. The estimated time constants are a little larger in the first period than in the second, dropping from 1 to 0.8 days.
It was tested whether the gAvalue can be assumed to be the same for the two periods. The model fit is based on the assumption of Gaussian noise, and hence, the test becomes an F test. The p value is 8.1%, which means that the difference in gAvalues over the two periods is statistically insignificant. Hence, the models with common gAvalues could be used.
A fundamental assumption of ARMAX models is that the residuals are independent. Therefore, the autocorrelation of the residuals must be checked. Sample autocorrelation functions of the residuals of the model with common gAvalues applied on the two data sets are plotted in Figure 8 together with confidence bands for white noise. The estimated autocorrelations are relatively small for both periods, and hence the dynamics of both data sets are well described by the fitted model.

Figure 8. Estimated autocorrelations of the residuals of the fits of Model (23) on the two data periods. Period 1 to the left, period 2 to the right. The dashed blue lines are confidence bands for white noise.

Using this simple ARX model, none of the properties of the building are significantly different between the two periods. It should be noticed that it is difficult to compare model fits on two different data sets. However, it demonstrates consistency in the results using this model. A clear weakness of the model is that averaging to daily values reduces the number of data points dramatically.
The averaging has another sideeffect that may cause problems. Figure 9 shows average solar radiation versus average indoor temperature for the two periods. For period 2, there is a strong correlation (more than 0.9), which means that the impacts of the two are hard to distinguish. An approach to overcome such issues is to excite the system better by varying the indoor temperature independent of other inputs. Section 4.3 introduces methods to avoid this kind of issue in future work.

Figure 9. Average solar radiation versus average indoor air temperature for the two periods. Notice especially for period two, the large correlation between the two.

In the spring 2011, new measurement equipment and a programmable logic controller (PLC) system were installed in the house. These facilitate online and centralized scheduling and surveillance of experiments. Air temperatures in all rooms, heating and ventilation inlet and outlet temperatures and flows are measured. Moreover open/closed sensors are installed on all exterior doors and windows, and CO_{2} concentration is measured in the apartment used for experiments.
A weather station taking meteorological measurements is installed onsite. Ambient temperature and horizontal solar radiation as well as wind speed and direction are measured. An overview of the measurements most relevant to modeling the heat dynamics is provided in Table 5 . Meteorological data is also available from the governmental weather station nearby used for analysis in this paper.
Measurement  Common areas  Rental apartment  Experimental apartment 

Indoor temperatures  All rooms  All rooms  All rooms 
Full standard indoor temperature measurement in living room  
Heating  
Floor heating  2/2  5/5  5/5 
Ventilation after heating  All measured together  
Ventilation  
Central ventilation  All measured together  
Outer doors open/closed  2/2  3/3  3/3 
Windows open/closed  No windows  2/2  2/2 
Cooker hood  0/0  0/1  1/1 
Occupancy indicators  
PIR sensors  0  0  Living room/kitchen, corridor 
CO_{2} concentration  0  Deactivated  Yes 
Consumption  
Oil  All measured together  
Electricity  1/1  1/1  1/1 
PV system  Only one system  
Total heat collection  
Domestic water heating  
Buffer water heating  
Heating system  Contributes to common system  
Metereological variables  All at one common weather station  
Ambient temperature  
Solar radiation  
Wind speed  
Wind direction 
With the new control system, heating and ventilation systems can be controlled based on all measurements, functions hereof, or even exogenous inputs. An overview of the state of the system is available online, and a screen dump of this is seen in Figure 10 . The overview intuitively shows how the different systems are connected and interacted. There are two circulation systems, illustrated by different colors of the pipes. Follow the one leading from the boiler; it goes to the domestic hot water tank (if the return valve is open), to ventilation after heating, and/or to floor heating. Before it comes back to the furnace, it passes through a heat exchanger. The other pipe system goes from the solar panel. It goes to either heating the domestic water tank or to the radiator and buffer tank when a surplus of heat from the solar panel is present. The storage tank is both loaded and unloaded from the top so that a vertical temperature gradient can be maintained in the tank.

Figure 10. Overview of the most important flow and temperature measurements in the house.

Formulation and selection of a statistical model is an iterative process, and when modeling systems of high complexity it is often fruitful to start from a simple description and then stepbystep include new terms if they significantly improve the description of the system. An initial description of the heat loss was given in the preceding section. In order to describe the heat dynamics in more detail, graybox models (Madsen and Holst, 1995 ; Andersen et al ., 2000 ; Bacher and Madsen, 2011 ) can be applied. Graybox modeling combines the advantages of using physical knowledge about the system with statistical methods to obtain precise descriptions of the dynamics behind measurements of a physical system. The stochastic differential equations used are based on the wellknown differential equations of heat dynamics which are naturally dynamic. A very simple linear dynamical model of the indoor temperature, Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_i}
, is formulated in (Bacher and Madsen, 2011 ):

( 24) 
where Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_i}
is the indoor temperature, R is the thermal resistance of the building envelope, Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle C_h} is the heat capacity of the building, Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle A_w} is the effective area of the windows, and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle P_h} is the heat supply from the heating system. Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\omega }_i} is a standard Wiener process (a white noise process in continuous time), and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\sigma }_i} is a constant. Eq. (24) describes the indoor temperature evolution in continuous time.
Let Y (n ) be the measurement of the indoor temperature at discrete time n :

( 25) 
i.e., the measurements are encumbered with white noise, e (n ). For indepth treatment of stochastic differential equations, see Øksendal (2007) . For filtering, i.e., reconstruction and prediction of the temperature based on measurements, see Jazwinski (2007) .
The test facilities available for the project are expected to enable more detailed observation of the heat dynamics. Hence a more general dynamic heat balance in the house is considered. Let P in general denote a heat flux, and the subscripts h , v , c , s , and i denote the heating system, ventilation, conduction, solar radiation, and infiltration respectively. Then

( 26) 
expresses the interior temperature development. Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\sigma }_2}
is a constant and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle {\omega }_2} is a standard Wiener process.
The conduction Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle P_c}
through walls, roof, doors and windows is expected to be of major importance. Let this be an example of how the model can be extended to contain more states, i.e., consist of coupled stochastic differential equations. Let it be given by a conduction from the outside surface temperature of the building, Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_o} , and the indoor temperature:

The outer envelope surface could be cooled (or heated) as modeled by convection. Then that state could be written as follows:

( 27) 
where f_{W} could be a nonlinear function of wind speed and wind direction. In Jiménez et al. (2008b) with a model similar to this one, f_{W} is modeled for a PVmodule with an allometric function. Further extension in the present case could include dependence on the wind direction.
This nonlinear extension of the linear dynamic model is only one of many possible extensions. It has been justified from physical considerations but the main criterion is the ability to describe the behavior of the system, i.e., what is reflected in the data. Hence, standardized model search procedures as in Bacher and Madsen (2011) are needed.
Estimation of parameters in graybox modeling requires – depending on the complexity of the models – not only good models, but also good experiments. Parameter estimates can be correlated if parametrization or the experimental plan is suboptimal. Take Eq. (24) as an example. If Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle T_i}
is constant, R and Failed to parse (MathML with SVG or PNG fallback (recommended for modern browsers and accessibility tools): Invalid response ("Math extension cannot connect to Restbase.") from server "https://mathoid.scipedia.com:8081/localhost/v1/":): {\textstyle C_h} turn out not to be identifiable. Therefore, the indoor temperature has to be varied. For being able to distinguish influences from each other, the input signal (here, the floor heating) must be varied on all frequencies, which can be done using PRBS (PseudoRandom binary signals) or ROLBS (Randomly Ordered Logarithmically distributed Binary Sequence) signals. The system is said to be excited. This was the focus of experiments that were carried out in 2012. Such input signals are said to be persistently exciting.
Statistical modeling of heat dynamics is a strong tool for characterization of and improving energy performance of buildings. A framework of linear dynamic models (ARMAX) was described together with methods to extract important information about heat dynamics from model estimates.
Promising results have already been obtained by applying linear dynamic models on heat dynamics in buildings. An example study was given where 2 periods of 2.5 months each were compared for a described low energy house in Greenland. Repair work was carried out between the two periods, and improved tightness of the envelope was expected in the second period. Heat consumption was modeled using indoor temperature and weather variables, and properties of the building were estimated and compared over the two periods. From the available measurements, the expectation that repair works had made the heating consumption in the building less sensitive to wind could not be demonstrated.
However, long testing time was needed, and separating impacts of different inputs seemed to lead to problems. Test facilities in the Arctic area have been described and the advantages of these in relation to more detailed modeling have been discussed. Finally, some examples on modeling, nondynamic and dynamic, linear and nonlinear have been given. Experiments will be carried out to apply models of this framework on experiments carried out in 2012.
Published on 12/05/17
Submitted on 12/05/17
Licence: Other
Are you one of the authors of this document?